The generators are characterised by their nominal extinguishing capability, expressed as the volume of space in which the amount of emitted aerosol from the generator, ensures extinguish flammable liquid fires or fire localization of solid combustible materials. The nominal extinguishing capability corresponds to the test area with a precisely defined small leaks and calulated value is 50 g aerosol to one cubic meter. If there are leakages in the particular protected space that cannot be closed in the case of fire, or protected space is of extraordinary configuration, it may be necessary to increase the aerosol concentration and the required number of the generators GHA is determined by the project after a detailed calculation.
Protection rooms. They can be combined into sets of up to five pieces and they are hung on a simple steel construction placed on the wall.
Nominal extinguishing capability 20m³
Generator Weight 3,7kg + 0,3kg
Filling weight 1kg
Generator height 115mm
Generator diameter 162mm
Protection of technological space where they stand freely, or they are situated in suitable place . They are not adapted for installation into sets.
Nominal extinguishing capability 4 m³
Generator weight 1,2 kg
Filling weight 200 g
Generator height 88 mm
Generator diameter 90 mm
Nominal extinguishing capability 10 m³
Generator weight 7 kg
Filling weight 1 kg
Generator height 334 mm
Generator diameter 180 mm